Honeywell C200 Controller - DCS Training Notes
Power supply in first slot - Slot x. Redundant PS configuration are available. Slot 0-9/0-16 in Controller chassis with FTEB(Fault tolerent ethernet / Control Net Interfaceas first module by default Redundant modules in same slot of redundant chassis as mandatory. FO(Fiber Optic) redundant link on RM(Redundancy Module) no I/Os permitted on redundant controller chassis except FIM & IOLIM(IO link interface module) I/Os permitted on non-redundant controller chassis Unique MAC IDs for CNI on process netwrok & supervisory network. No duplication on single (uplink OR downlink) network except for redundant modules. Max. 64 IO cards (Chasi/PM IO) supported No redundancy in Series “A” I/O (chasis I/O) 24 I/O modules supported per CNI. 4 CNI per controller. CNI MAC IDs set same for redundant controllers uplink & downlink CNIs. Base address+1 assumed for backup controller based on s/w configuration Server Addresses 23-“A” & 24-“B” by default. In case of ACEnode on CNI n/w, ACEnode shall have adddress 24 & servers shall be assigned 31 & 32 address respectively. PS output is 24V, 3V, 5V, 1.2V Pulse Input not supported, I/O redundancy permitted as per xPM I/O redundancy SIM on Series “A” I/O only, as a Serial Input Processor. PIM on series “A” I/O only, as a Pulse Input Module.